Test Section: Downstream - PTD The duct mounted downstream sample test section shall be designed to perform an aerosol test on HEPA filters, and a vapor test on carbon adsorbers. Test section shall have a concentric sample pipe array to obtain representative concentrations downstream, when testing HEPA filters or Carbon Adsorbers. The test section housing body shall be fabricated from 304/304L stainless steel products. The array shall be of aluminum alloy or 300 series stainless steel construction. The test shall be bolted or quick clamped to the exit ductwork and adjacent housing or downstream damper assembly. The interface connection of the injection pripe array shall be female 3/8” NPT with a brass plug. The test section shall be able to perform the applicable acceptance or surveillance tests as required per the intent of ASME N510-1995 Reaffirmed and IEST RP-CC0034.3. Maximum pressure drop through the downstream test section shall be 0.200" water gage at a total system velocity of 1,000 feet per minute (fpm).