Output Circuit Breakers. Specify quantity and rating.
Fast charge: A battery charger upgrade which decreases the time to recharge a fully discharged battery bank to a full charge. Recharge time is reduced from the standard 24 hours to 12 hours.
Summary Form C Contacts: Form “C” contacts rated at 5 amps. Dry contacts will change state when any system alarm activates. Examples include battery charger fault, low battery voltage, load reduction fault, output overload, and high/low AC input voltage.
Maintenance Bypass Switch: An internally mounted switch permitting bypass of the inverter to the load, allowing isolation of the inverter to allow direct connection of the load to AC utility input so routine maintenance may be performed.
External Bypass Switch: An externally mounted switch permitting bypass of the inverter to the load, allowing isolation of the inverter to allow direct connection of the load to AC utility input so routine maintenance may be performed.
Factory Turn ON: Contracted turn on by the factory, to maintain the full warranty of the system.
Remote Meter Panel: Externally mounted remote meter panel to provide remote access to all system parameters.
Dry contacts to provide signal for system failure alarms.
Auto dialer, automatically dials up to 4 user programmed maintenance phones.
Run time, insert the number of minutes after the “R” for non-standard run times (Standard is 90 minutes).
Output trip alarm, provides an audible and visual alarm when an output circuit breaker is opened or tripped.
Remote summary alarm panel.
RS 232 port (DB 9 ) Programmable monthly and yearly testing (meets NFPA 101 Life Safety Code requirements).
Office: 718-418-5600 • Fax: 718-418-5618 57-10 49th Place • Maspeth, N.Y. 11378 www.encorelighting.com