SHOP DRAWING / SUBMI TTAL REVIEW FORM No Exceptions Taken Make Corrections Noted REVIEW IS SOLELY FOR GENERAL CONFORMANCE WITH THE DESIGN CONCEPT. THIS REVIEW DOES NOT RELIEVE THE CONTRACTOR FROM TOTAL RESPONSIBILITY FOR QUANTITIES, ERRORS, OMISSIONS OR COMPLIANCE WITH THE INTENT OF THE CONTRACT DOCUMENTS. REVIEW AND APPROVAL BY CONTRACTOR IS REQUIRED BEFORE FABRICATION, SHIPMENT OR INSTALLATION. Revise and Resubmit ANY ACTION SHOWN IS SUBJECT TO THE REQUIREMENTS OF THE PLANS AND SPECIFICATIONS. CONTRACTOR IS RESPONSIBLE FOR: DIMENSIONS WHICH SHALL BE CONFIRMED AND CORRELATED AT THE JOB SITE. ALL REVISED SUBMITTALS MUST BE RETURNED BY CONTRACTOR WITHIN 15 DAYS FROM RECEIPT OF THE ORIGINAL SUBMITTAL REVIEW. Rejected Reviewed SUBMITTAL NUMBER/ REGISTER NUMBER : SUBMITTAL NAME: RELATED SPECIFICATION: DATE RECEIVED: REMARKS: 260923 and 260943 PROJECT NAME: Grand Junction MOB Lighting Controls Submittal Package CCRD PROJECT NO.: 812136 Electrical REVIEWER’S NAME: Kelly Hannegan 3/26/2013 DATE REVIEWED: 4/1/2013 1. Revise control power input to LCP to circuit 1EQLB-27 in lieu of 1LA-43 indicated on 2. 3. 4. 5. the drawings. Provide 20A 3P circuit breaker at Panel 1LA-80/82/84 in lieu of (3) 20A 1P circuit breakers. Provide 3/4"C 4 #12, 1 #12G feeder and connect to lighting control panel Phase Loss Sensor Panel (PLSP-1) per lighting equipment vendor specifications. Locate adjacent to LCP to suit field conditions. Revise 1-line system drawing to include indoor/outdoor photocells for final O&M submittal. Contractor shall be responsible to verify that dimmer switches indicated are compatible with lighting fixture dimming ballasts to be provided. Timer switches submitted are acceptable for use only in Janitor Closets. Provide wallbox-type occupancy sensors in all other areas as indicated on the drawings. END OF SUBMITTAL REVIEW From: Sent: To: Cc: Subject: Russell Tafoya <[email protected]> Monday, April 01, 2013 4:15 PM Brady McQuinn; James Selecky Ryan Bonner; Mike Murphy RE: Project: 112039.00 - Grand Junction Medical Center - Submittal Responded to and Clos... - Submittal:26092301-03, 26094301:4K4I0 Thank you Brady, Weifield Group response to the remarks in the submittal are as follows: Item 3: one line shows exterior photo cell only as the other light sensors in the building are line voltage stand alone sensors as submitted which do not tie into the lighting control panel. They provide on off function for the related adjacent lighting locally, typical of two locations. Item 4: confirmed, dimming technologies are coordinated in the boardroom. Item 5: We submitted the time switch to work for the trash enclosure location. We will furnish a weatherproof cover. Wallbox type occupancy sensors are shown in the janitor’s closet on the drawings. Please advise if this is direction to revise them to timer switches. Russell Tafoya, Senior Project Manager Weifield Group Contracting LLC 146 Yuma Street Denver, CO 80223 303.428.2011 office 303.407.6624 direct 303.847.8341 mobile 303.202.0466 fax www.weifieldcontracting.com LEEDing the way in electrical construction From: Brady McQuinn [mailto:[email protected]] Sent: Monday, April 01, 2013 4:03 PM To: Russell Tafoya; James Selecky Cc: Ryan Bonner; Mike Murphy Subject: FW: Project: 112039.00 - Grand Junction Medical Center - Submittal Responded to and Clos... Submittal:26092301-03, 260943-01:4K4I0 Russell and James, Please see the attached submittal. Thank you, Brady McQuinn Project Engineer Cell: (303) 356-3999 From: Jeff Beardsley [mailto:[email protected]] Sent: Monday, April 01, 2013 3:34 PM To: Brady McQuinn Subject: Project: 112039.00 - Grand Junction Medical Center - Submittal Responded to and Clos... Submittal:26092301-03, 260943-01:4K4I0 This email contains the response for a Submittal. The Submittal transmittal is attached to the email. Project Name: Project Number: 112039.00 - Grand Junction Medical Center 112039.00 From: To: CC: Jeff Beardsley (Boulder Associates, Inc.) Brady McQuinn (GH Phipps Construction Companies) Subject: Transmittal ID: Submittal ID: Remarks: Lighting Controls 00333 26092301-03, 260943-01 Transferred Files Name Type Date Time Size 260923-01-03, 260943-01 Lighting Controls.pdf Adobe Acrobat Document 4/1/2013 3:32 PM 4,366 KB Notification generated by Newforma Project Center Jeff Beardsley, AIA, LEED AP BD+C | Associate BOULDER ASSOCIATES ARCHITECTS | Design Leaders for Health & Aging 1426 Pearl Street, Suite 300 | Boulder, Colorado 80302 | 303.499.7795 | boulderassociates.com BOULDER | SACRAMENTO | ORANGE COUNTY | SAN FRANCISCO | DALLAS By accepting and using this information the recipient agrees to the following terms: The attached electronic files are provided for the purpose of expediting input of information into the recipients computer. In using or modifying this data, the recipient shall confirm the information matches the hard copy drawings and/or actual field conditions, if any. Boulder Associates hereby disclaims any liability related to the use of these electronic files, and does not guarantee any accuracy of the information. The information provided by Boulder Associates shall not be used for any purpose other than the project for which it was originally intended. These electronic files shall not to be released to any other party without the written consent of Boulder Associates. These electronic files are an instrument of professional services and shall remain the property of the parties listed in the professional services agreement.