THERMflow Double Pump Kit Wiring Diagram. (Gas/Oil Boiler and a Solid-Fuel Boiler) To be used in conjunction with the attached wiring instructions USING A DANFOSS PROGRAMMER FP715si 1 2 3 4 5 6 7 8 9 10 11 12 13 14 15 16 L N Switched live to boiler. Some boilers may require a permanent Live. Refer to boiler instructions for details. N N E E E To be wired on site Key Live Neutral Earth * On Fitted Double Pump Kits Only Boiler 5 core from Programmer Solid Fuel Stat. Central Heating Pump Boiler Pump Cylinder Stat. Pre-wired by McDonald Engineers * Switch Wire Switch Wire Switch from terminal 3 on programmer Switch from terminal 4 on programmer The anti-boil stat should be set at around 85 Deg C, and should have a switching differential of not more than 4 Deg C. This stat must be wired to M/O/R (make-on-rise), and should be positioned between 1/3rd and ½ way up the THERMflow.