Load Shedding Relay Module Model: LS101X1SD Latching 200 Amp Disconnect Switch IMPORTANT: Magnetic Relays require power to change state. There is also a delay of one minute seconds between cycles. Wiring Configuration for Loss Of Utility Load Dropping Input from breaker or disconnect switch 1) When 120 Volts AC is applied to the control input of the control board the latching relay will toggle to the on state after a 5 Minute delay. 2) When power is removed from the control input the relay will toggle OFF after a 3-5 second delay. Line Neutral 120 Volt AC Control Input Voltage From Utility Line Side Of Transfer Switch Output to load 6QT EQPFKVKQPU QVJGT VJCP VJQUG FGUETKDGF CDQXG# RNGCUG EQPVCEV C PSP Inc. 1EEQWPV =GRTGUGPVCVKXG CV !800" 648-6802 # QT 61B (703) 368-8376 QT YYY%surgeprogram%EQO 8B<GD OHN @HK =BHHLCGA JN<ECMO IKH>N=ML @KHF PSP Products Inc.