CODE ISSUES FROM PREVIOUS MEETING When wiring a residence for a free standing gas and electric range and the owner elects to use the gas range outlet, is it permissible to terminate 240v conductors in a junction box and leave them terminated on the breaker or do you need to install the range receptacle? If you land the wire on a breaker, the range receptacle must be installed. This would also apply to a gas and electric dryer. The only time the 240v wiring will be permitted to be terminated in a jbox is if you leave the wire off the breaker in the panel. Do you have to change a range cable from 3 wire to 4 wire when you replace the oven and range? If you do not have to relocate or extend the circuit and you are replacing the range/oven, you can leave the three (3) wire cable as is. If the kitchen is being remodeled it must be changed to a four (4) wire cable and outlet. Are we requiring the overhead light on a porch to be installed if there is a coach light installed at the door? Must light be installed over a garage door or beside the garage door on a final? If these fixtures are not the required fixture it is permissible to blank the fixture off. What is the allowable fuse on a #2 cu run to an A/C unit? Would 100a amp be allowed? No. Can not use 310.15(B) (6) to figure the wire size to an A/C unit. 90a would be the allowable fuse.