MITIGATION MEASURES FOR GNERATOR/SOURCE OF ENERGY As per para 19 of provided checklist Mitigation Measures for Generator/Source of Energy are described below: GENERATOR: The combustion processes for generator will not be significant to affect the ambient air quality of the area. Any exhaust emissions will disperse with the prevailing wind currents and will not have any significant impact on the local air quality. Moreover complying with the mitigation measures stated below will further result in the reduction/prevention of these emissions. Mitigation Measures The stack height of the generator during operation phase will be vented through vertical stacks to minimize exposure at ground level; The stack height of the generator will be: H = h + 0.2 .JKVA, H = Total stack height in meters. h = Height of the building in meters where or by the side of which the set is installed. The generator will be properly tuned and maintained in good working condition in order to minimize exhaust emissions; Diesel with the low sulfur content will be used as fuel in the generator in order to reduce SO2 emissions Residual Impacts The residual impact will be insignificant once the mitigation measures are carried out. Monitoring Requirements Periodic monitoring of stack emissions from the generators will be carried out and recorded to ensure continued compliance with NEQS.