Technical Data INS # Linear Dimming Control Module Catalog# Prepared by Project Date Comments Type Overview Linear Dimming Control Module Plenum Rated (LDCM-PL) takes a 0-10V dimming dignal and a fixed line voltage input and converts it to an ELV dimmed output for up to 1000W with a 277V load and 450W on a 120V load. One LDCM can be used per run up to the maximum wattage. The LDCM-PL is rated to directly mount to a junction box in a plenum space for easier installations and to meet building requirements. Features Dims ELV only fixtures with 0-10V Simple Installation Direct J-Box Mount 120V and 277V compatible Auto-Sensing Voltage Switch 450W @120V, 1000W @277V Plenum Rated One LDCM per fixture run Technical Data July 2016 Specifications ELECTRICAL Power Rating Max Fixture Run Length Operating Voltage Operating Hertz Startup Temperature Operating Temperature Storage Temperature Dimming CONTROL Requirements PHYSICAL RATING & CERTIFICATIONS Dimensions Housing / Lens Connectors Weight Environment Mounting Options ETL / cETL Damp Locations 450W Max @ 110-120V 1000W Max @ 277V Calculate Maximum Run per LDCM unit based on the Power Consumption of the fixture used. 110VAC-120VAC, 277VAC - Auto-Sensing Voltage Switch 60 Hz -4°F to 104°F (-20°C to 40°C) -4°F to 104°F (-20°C to 40°C) -40°F to 176°F (-40°C to 80°C) 110-120VAC; ELV (forward/reverse) - RP; converted from 0-10V Controller 277VAC; ELV (forward/reverse) - RP; converted from 0-10V Controller W 3.4” x H 2”” x L 7”; (87mm x 50mm x 178mm) Injection Molded Polycarbonate Lead Wire 6” From Conduit 0.99 lbs (0.45 kg) ETL Damp Location Conduit Mounting For Both Sides RoHS COMPLIANT This product is provided by Eaton Lighting Solutions in cooperation with EcoSense Lighting Inc. Ordering Choose the option that best suits your needs and write its corresponding code on the appropriate line to form the product code. LDCM-PL MODEL 120-277 VOLTAGE 010V CONTROL LDCM-PL 120-277 010V-0-10V 110VAC-120VAC,277V Auto-Sensing Voltage Switch GR COLOR GR - Grey EXAMPLE: LDCM-PL - 120-277 - 010V -GR Dimensions 7.0in 178mm 5.4in 138mm 0-10V DATA IN 3.4in 87mm 110VAC-120VAC, 277VAC POWER IN 110VAC-120VAC, 277VAC + ELV DATA TO FIXTURE RUN 152mm WIRE 6in 152mm WIRE 2.0in 50mm 6in 1/2-14 NPS Thread 2 www.eaton.com/lightingsystems Technical Data July 2016 Connections LDCM NOTE: The EcoSense LDCM module takes a 0-10V dimming signal and fixed line voltage input and converts it to a ELV dimmed output for up to 1000W @ 277V or 450W @120V. The LDCM is rated to mount directly to a junction box in the plenum space for easy installation. RED GREY HOT NEUTRAL LDCM BLACK YELLOW 120V receptacle circuit WHITE Sensors Sensors Slider Station Wallstations + + A/V Mode + Demand Response + Alert Mode Time Clock Adjustable Skylights 6 5 Blue Red 4 Integration Controls QuickConnect Cables Adjustable Skylights Switchpack Receptacle BMS/Out Black Brown Dual Technology Wall Corner Occupancy/Vacancy Sensor (OAWC-DT-120W) OCC-RJ45 (Occupancy Coupler) 3 2 1 3 4 Reset Not Used Occupancy Occ Vac (default) Energy Options 2 Status Low End 1 High End Energy Options DIP Switch Demand Response Default 10% 20% 30% 40% 0-10V Gain Adjustment BLUE - Emergency Power In (120/277VAC) Green Integration Controls Red - Load 2 Out Purple - Load 3 Out Blue - Load In Yellow - Load 1 Out Black - Line In White/Black - 120V N White/Orange - 277V N YELLOW Emergency Power OUT Black Daylight sensor (DSRC-FMOIR) Model: OCC-RJ45 Occupancy Sensor Coupler BLUE - Relay In (120/277VAC) White Red CAUTION: Bonding between conduit connections is not automatic and must be provided as part of the installation. WHT/ORG or WHT/BLK Neutral BLACK - Hot (120/277VAC) SPRC-R-20-120 20A Receptacle Control Blue - EM Line In Blue - EM Loads Out ELV LIGHTING LOAD (1) 0-10V Dimming Outputs + + + Dimmer 3 Dimmer 2 Dimmer 1 Dimmer 3 + - Dimmer 2 + - Dimmer 1 + - 0-10V Dimming Button 1: Load (1),(2),(3) ON, Dimmer 1: 100%, Dimmer 2: 80%, Dimmer 3: 100% Button 2: Load (1),(2),(3) ON, Dimmer 1: 80%, Dimmer 2: 20%, Dimmer 3: 100% Button 3: Load (1),(2),(3) ON, Dimmer 1: 50%, Dimmer 2: 100%, Dimmer 3: 25% Button 4: Press and Hold Raises all dimmers Button 5: Press and Hold Lowers all dimmers Button 6: All Loads OFF Violet - Dimmer 1 Gray - Dimmer 1 Scene 1 Zone 1 UP Scene 2 Zone 1 DN Scene 3 Zone 2 UP Raise Zone 2 DN Lower Zone 3 UP All Off Zone 3 DN Button 1: Press and hold increase Zone 1 lighting 5% Button 2: Press and hold decrease Zone 1 lighting 5% Button 3: Press and hold increase Zone 2 lighting 5% Button 4: Press and hold decrease Zone 2 lighting 5% Button 5: Press and hold increase Zone 3 lighting 5% Button 6: Press and hold decrease Zone 3 lighting 5% RC-6TSB-P4-* RC-6TSB-ZAD-* Scene Station Office Station Scenes are programmable within the Room Controller using the Personal Remote (HHPR-RC) and new programming is accessed through the Scene Wallstations. Eaton 1000 Eaton Boulevard Cleveland, OH 44122 United States Eaton.com Eaton Lighting Systems – Controls Products 1121 Highway 74 South Peachtree City, GA 30269 eaton.com/lightingsystems © 2016 Eaton All Rights Reserved Printed in USA Publication No. TD503075EN July 19, 2016 Eaton is a registered trademark. All other trademarks are property of their respective owners.